Boiler Pressure Parts High Temperature Superheater Wiht 304 Shields
Superheater is the part that heats the steam from the saturation
temperature to the superheater by the boiler. It is also called the
Superheater can be divided into convection type, radiant type and
semi-radiant type according to heat transfer mode;
According to the characteristics of the structure, it can be
divided into serpentine tube type, screen type, wall type and wall
They all consist of a number of parallel pipes and inlet and outlet
Most industrial boilers do not have superheaters because many
industrial processes and utilities require only saturated steam.
Superheaters are generally installed in power stations, locomotives
and Marine boilers to improve the thermal efficiency of the entire
steam power plant.
Super heater types:
1. Radiant super heater: it is the earliest type of super heater
and it is located above or behind banks of water tubes to
protection them from direct flam or fire.
Parameters that increases the convection
a. Increasing the fuel-and air flow (combustion gas flow)
b. Increasing the mass flow rate of the steam
Radiation is mainly dependent on the flam temperature. as the steam
flow rate increases the exit temperature become lower.
Radiant super heater
They are placed exposed to the heat source whcih requires the
improvement of metal temperatures.
Radiant and convetive super heaters and reheaters are used for high
The accessory of high temperature radiant steam super heater in
It is made up of snake-like tubes (carbon steel, alloy steel or
heat-resistant steel, etc.) and collection boxes and other
supporting material. Tubes generally have φ32, φ38, φ42 or other
types of specifications, according to user's needs separately.
They are the sane as the super heaters but as their exit
temperature is a little bit less than super heaters and their
pressure is 20% -25% less than the super heater, they can stand
less quality material alloys.
Steam super heater is consisted of dense tube coils and is placed
in the flue under the tempearture 450ºC-1000ºC.
For power plant boiler capacity over 10Mpa, platen and coiled
superheater are usually adopted.
What are the differences of Superheater And Reheater?
|Pendant-type||1.Firm structural support||1. Flow blockage by condensed steam 2. Needs slow restart to purge
the water that accumulates in the bottom.||supported from above|
|Inverted-type||1.Proper drainage of the condensed steam||1. Lack the structural rigidity, especially in high speed gas flow||Supported from below|
1. Proper drainage
2. Good structural rigidity.
|1. They do not view the flam directly so they are mainly from the
convective type||Usually supported in the vertical gas ducts parallel to the main
|structure||horizontal or vertical|
|material||carbon steel, alloy steel|
|tubes||φ32, 38, 42, etc.|
- 1. heating saturated steam, temperature up to 900 degree C.
- 2. high efficiency, >90%.
- 3. high speed heating.
- 4. design with stainless steel.
- 5. long design service life, 15 years.
Send us required technical data, such as steam capacity, presure,
required temperature etc. We will design accordingly.
HD Boiler offers a best in class facility
For over 30years, Hua Dong Boiler has been consistently innovating
and improving our boiler superheaters and reheaters.The
improvements in bending,welding and design ensure our products meet
both Euorpean and American standards, ensuring a relabile